Harmonics in Offshore Electrical Power System
- Balesh Kumar (Kvaerner E&C) | Vinod K. Sethi (Kvaerner E&C Singapore Pte Ltd) | Saibal Bhattacharjee (Kvaerner E&C)
- Document ID
- Society of Petroleum Engineers
- SPE Projects, Facilities & Construction
- Publication Date
- March 2006
- Document Type
- Journal Paper
- 1 - 6
- 2006. Society of Petroleum Engineers
- 4.1.2 Separation and Treating, 4.2.3 Materials and Corrosion, 1.6 Drilling Operations, 4.5 Offshore Facilities and Subsea Systems, 3.1.2 Electric Submersible Pumps, 3.1 Artificial Lift Systems, 1.6.9 Coring, Fishing, 5.4.6 Thermal Methods, 1.10 Drilling Equipment
- 2 in the last 30 days
- 381 since 2007
- Show more detail
- View rights & permissions
|SPE Member Price:||USD 10.00|
|SPE Non-Member Price:||USD 30.00|
Recently, electrical submersible pumps (ESPs) have become widely used in depleting oil fields with low pressure (dead crude) and in deep wells with marginal pressure to achieve oil production. These types of ESPs are variable-speed drives (VSDs) and operated at variable voltages and frequencies to optimize production. The introduction of a large amount of ESPs driven by VSDs into an electrical power system of an offshore oil field that is electrically weak leads to distortion of voltage and current profile beyond acceptable limits, thereby producing harmonics. The more distortion there is in the waveforms, the higher the harmonics.
The concept of harmonics, along with their impact and mitigation measures to be exercised in an offshore power system, is discussed in this paper. Furthermore, a method statement is provided for sizing the active harmonic filter (AHF). An attempt is made to arrive at an empirical relationship for an AHF rating in kVAR for offshore electrical power systems, but it is not yet well documented. A case study of harmonic analysis for an integrated offshore field in the South China Sea has been discussed.
The information contained in this paper is useful for design engineers as well as operators handling electrical power systems for offshore oil fields with significant amounts of nonlinear loads or VSD loads. This enables them to predict the requirement of harmonic treatment in offshore electrical power systems. It also helps them to take early action at the planning/design stage to avoid probable damage to equipment or loss of power resulting from harmonics and to conduct detailed harmonic analysis.
A highly reliable, high-quality power supply is of paramount importance in offshore oil and gas installations. Power outages and poor power quality have resulted in considerable cost in these installations. Power quality is defined in terms of voltage variation, voltage transients, and voltage waveform. One of the power-quality characteristics lies in its waveform. It is preferred to have a power-supply waveform as close as possible to that of a pure sine wave. In reality, the power-supply waveform is never purely sinusoidal. The power-supply waveform gets distorted because of nonlinear loads, rectifiers, VSDs, arc furnaces, fluorescent tubes, discharge lamps, fan regulators, and other power-distribution equipment. The waveform distortion is identified as a combination of fundamental sinusoidal waveforms and harmonics.
Harmonics are pollutants and impact the quality of power and the life of the electrical equipment. They need to be contained and can be contained by adopting the mitigation measures discussed in this paper. It has long been recognized that harmonic currents and voltages are highly detrimental to electrical power equipment and systems. Their presence can damage equipment and disrupt the production process, thereby costing the offshore oil and gas operators tremendously.
|File Size||752 KB||Number of Pages||6|
G.5/4. 2001. U.K. Electricity Council Engineering Recommendations.
Guide to Harmonics with AC Drives_ABB, technical guide No.6.
IEC 61000 2-2. 2002. Compatibility Levels For Low Frequency Conducted Disturbances and Signaling In Public Low-Voltage Power Supply System, IEC.
IEC 61000 2-4. 2002. Compatibility Levels In Industrial Plants for Low Frequency Conducted Disturbances, IEC.
IEC 61642. 1998. Industrial AC Networks Affected By Harmonics—Application of Filters and Shunt Capacitors, IEC.
IEEE 2000. Draft Guide for Application and Specification of Harmonic Filters, IEEE.
IEEE 399. 1997. Recommended Practice for Power System Analysis, IEEE, Brown Books.
IEEE 519. 1992. Recommended Practice and Requirements for Harmonic Control in Electrical Power Systems, IEEE.
IEEE C57.110. Recommended Practice for Establishing Transformer Capability When Supplying Nonsinusoidal Load Current, IEEE.
PES. November 1982. Sine Wave Distortions on Power Systems and the Impact on Protective Relaying. Draft #5. Power System Relay Committee of the PES Report.
Read, J.C. 1945. The Calculation of Rectifier and Converter Performance Characterstics. J. of IEE 92 (II). 495-509.
Rice, D.C. Adjustable Speed Drive and Power Rectifier Harmonics—Their Effect on Power System Components. IEEE paper PCIC-84-52: 269-287.
Wood, W.S. 1974. Effects of Supply Voltage Waveform Distortion on Motor Performance. Paper presented at the Intl. Conference on Sources and Effects of Power System Disturbances, London, 22-23 April: 261-267.